Tips for proper installation
All headless screws in corner connections, cross connections and passageway connections as well as transformers must be tightened firmly. All cable connections with external feed should be checked for tightness. The knurled-head screws of the spotlights must firmly be tightened, even if the lamp already has contact. All illuminants should be checked for a solid seat when inserting. The current relay must be activated by pressing the memory key for taking over the nominal load.
The distance of the conductor rail from the ceiling or the wall amounts to min. 6cm. To avoid bending the rail by own and spotlight weight, the distances between the fastenings should amount to on the ceiling max. 0.70m and on the wall max. 0.50m.
For safety reasons no objects may be attached to the conductor rail to the decoration or the like.
Current relays or overcurrent protection switches and transformers should be mounted easily accessible. The transformer used externally should be installed at the rail feeding as near as possible.
Information on transformers
The given transformer capacity determines the number and the capacity of the illuminants.
12V / 105VA transformer = 3 x 12V / 35W bulbs
Pay attention to the minimum load of the transformer:
transformer capacity 105VA :: minimum load 60W
transformer capacity 210VA :: minimum load 120W
transformer capacity 300VA :: minimum load 220W
Please note that with the utilization of the transformer the resistance of the busbar and connections are taken into account.
For safety reasons only Sölken transformers which are equipped with a protective device have to be installed.
Ceiling fasteners with further wiring
Spacing of fasteners
The distances between the fasteners (here ceiling fastener 9113 with gateway conductor 9205) should amount to max. 0.70m on the ceiling.
With horizontal arrangement of the bus conductor rails on the wall the distances between the fasteners should be not greater than 0.50m.
New feeding and separation with distance bolt 9206
Here the gateway conductor 9205 must get separated. Then screw together the secondary connection (12V) in the separated gateway conductor.
Max. cross-section 2,5mm2.
Owner: Stefan Schrader
Luruper Hauptstr. 125
Tel.: 040 - 831 99 64
Fax: 040 - 832 10 353
Mo - Fr 9 a.m. - 6 p.m.
Sa 10 a.m. - 1 p.m.